First, let’s define service facilities (per plumbing code). This would encompass anything from routine car cleaning and detailing, to full blown engine repair. "Service" applies not only to vehicles, but also to any kind of machinery that could leak oil into the building drainage system.
Both UPC and IPC recognize the following to calculate the capacity of an oil separator: (6) cubic feet for the first 100 square feet of drainage area, plus (1) cubic foot of required capacity for each additional 100 square feet.
Here's an example:
Oil change facility with 900 square feet of drainage area.
Keep in mind that some jurisdictions have their own requirements: 500 gallons, 1000 gallons, double-wall mandate, only allow concrete, etc.
If this is the case in your territory, let's work on changing that.
Below is a quick reference sizing chart that can found on page 3 of our 2017 Catalog.
We get it. Time is valuable and you don't want visit a webpage or receive an email that isn't relevant to what you do. This page is for you. All content is chosen by us and what we feel would be beneficial to our specifying partners. We also send out an email every so often.
engineer specialists: (206) 257-3387